36.21.640 WELL CASING
(1) All casing installed, other than plastic casing as set forth in ARM 36.21.641 and 36.21.645, shall be steel, in new or like new condition, being free of pits, breaks, or contamination, and shall meet minimum American Society of Testing Materials (ASTM) A53 specifications for line pipe for the following sizes:
Table 1 - Minimum specifications for steel well casing.
(2) All casing having a diameter larger than 20 inches shall have a wall thickness of at least 0.375 inch.
(3) Well casing installed in a well greater than a nominal diameter of ten inches, may have a wall thickness of 0.250 inch as long as it otherwise meets ASTM A53 specifications and does not exceed the following depth limitations:
Table 2 – Diameter and depth limitations.
(4) Casings of other specifications may be considered under the provisions of variances ARM 36.21.680.